Generally, it is optional with 2MM 304 stainless steel mounting panel for the differential pressure gauge. . After installation, there is no exposed parts, the overall appearance is beautiful, and the installation and maintenance are convenient.
The pressure difference is detected between the clean room and the non-clean room. The installation position is generally the wall between the clean room and the non-clean room, which is convenient to see from the outside.
The pressure difference between the inside and outside of the clean room, the red oil type differential pressure gauge should pay attention to the horizontal installation of the pointer type differential pressure gauge when installing, and pay attention to the pressure.
The high pressure pipe of the differential meter is connected to the high pressure room and the low pressure pipe is connected to the low pressure room.
If the clean room is a positive pressure chamber, then the high pressure end of the differential pressure gauge is connected to the clean room, and the low pressure end is not connected;
If the clean room is a pressure chamber, connect the low pressure end of the differential pressure gauge to the clean room and the high pressure end.
Previous: No Information
- Automatic Control Of Submersible Pump Start-sto...
- Key Float Switch
- Precautions For Liquid Level Controllers
- Key Features Of The Liquid Level Controller
- Differential Pressure Switch Technical Parameters
- Types Of Pressure Gauges
- Common Problems And Solutions Of Pressure Gauges
- Selection Principle Of Pressure Gauge
- Use Of Differential Pressure Gauges
- The Main Structure Of The Pressure Gauge